Shock chlorination is the easiest, cheapest way to sanitize well water that has been contaminated.
Sourcing your home’s water from a well means that you likely get to enjoy water that tastes far better than city-supplied water. But it also means that you are responsible for maintaining your system to ensure that you continue to enjoy safe, healthy water. Failing to monitor water quality can expose you and your family to harmful bacteria that can make you sick, or even cause damage to your well.
This is why all well water must occasionally be treated with chlorine bleach, through a process called “shock chlorination.”
Shock chlorination is the easiest, cheapest way to sanitize well water that has been contaminated with:
Chlorinating your well is quite simple, as all it requires is adding chlorine bleach to the water in your well. By adding chlorine to your well, the pH of the water is raised to a point that is toxic to bacteria and pests, killing them in a matter of hours.
If you have performed a water test that has come back positive for coliform bacteria, then it’s time to chlorinate you well. If you haven’t tested your well in a few years, it’s a good idea to test your water. But homeowners often wait until signs of a problem surface before testing their water. Common symptoms of bacterial growth in well water include:
A water test will indicate whether the issues you are seeing are symptoms of bacteria in your well.
Before you do anything, be sure to catch up on any bathing or laundry you need to do, and make sure you have adequate drinking water on hand. Once you have shocked a well, avoid bathing or doing laundry for at least 24 hours, if not longer.
The amount of bleach needed to shock a well depends on the size of your well. you need to calculate how much bleach you need. The rule of thumb is to add 3 pints of bleach (3/8 gallon), plus 3 pints for every 100 gallons of water in your well.
If you’re not sure how much water your well holds, you can calculate that yourself. Refer to the documentation provided to you by the company that drilled your well to determine its full depth. If you’ve lost the paperwork, contact them.
Once you know how deep your well is, determine the distance between the ground’s surface and the top of the water level. Subtract this from the full well depth. The resulting number is the water depth of your well. For instance, if your well is 300 feet deep, and the water starts 30 feet down, then the water depth is 300 – 30 = 270 feet. Now, refer to the following table.
Drilled/Bored Well Storage Capacity – Gallons Per Foot:
Multiply the water depth of your well by the gallons per foot indicated above. This is the total water volume in your well. For example, if the water is 270 feet deep, and your well is 6” in diameter: 270 x 1.5 = 405 gallons.
As we said before, you need 3 pints of bleach per 100 gallons of water, plus an additional 3 pints. In this case, 405 gallons is pretty close to 400, so we’ll just round down to 400. Divide the number of gallons of water by 100, then multiply by 3, and then add 3, to get to the number of pints of bleach you need. In this case:
In the case of our example, we need 15 pints of bleach, or 1 7/8 gallons.
Important note: You do not need special bleach to shock a well. In fact, you should avoid any special scented or gel bleaches. Don’t buy any the fancy stuff. Chances are, the cheapest generic bleach you can find will be perfect.
Once you have your bleach and know how much you need, clean out any debris in the well house or storage tank. Switch off the pump circuit breaker and remove the well cover.
Before you do anything else, you’ll want to sanitize the area just inside the well cap, as bacteria often builds up there, and failing to remove it will result in recontamination. Make a mixture of 10 parts water to 1 part bleach. Use this mixture to scrub as much of the inside surface of the well as possible. Scrub the cap as well. If the cap is in bad shape and will not form a seal when replaced, purchase a new one.
Now, you’re ready. Take the amount of bleach that you calculated above and pour it into the well. If you can, try and coat all the interior walls of the well with the chlorine, to sanitize the exposed surface.
Turn the breaker on, then run a garden hose—make sure the end is clean—into the well and turn on the hose faucet. Allow the hose to run until you can smell chlorine in the water. This may take anywhere from ½ hour to 2 hours. Then allow the hose to run for a few more minutes. Take the opportunity to use the hose to rinse the inside surfaces of the well casing, washing bleach and any bacterial buildup into the chlorinated water where they can be sanitized.
The water in your well is now nicely chlorinated, but the water in the pipes throughout your home is still contaminated. One at a time, will need to run every faucet in and outside your home, both hot and cold, until you can smell chlorine in the water. Run all shower faucets and showerheads. Flush all your toilets. Dishwashers and laundry machines should be run once as well. If running a faucet does not produce a chlorine smell, pour an additional 3 to 4 pints of chlorine into the well and try again.
Once you have run all your home’s taps, turn the pump circuit breaker off, and leave everything as it is for 24 hours. The chlorine in the water will gradually sanitize your system, killing all the bacteria in the water.
After you’ve allowed 24 hours to pass, turn the circuit breaker back on, and run each of your outside faucets, one by one, until you can no longer smell chlorine in the water. For the first outdoor faucet, this may take an hour or two. Be sure to run the hose out to a safe area where the chlorinated water won’t harm plants or animals.
If you have a low production well, run the hose for an hour, turn it off for two hours, and repeat as necessary. Then run each indoor faucet until you can’t smell chlorine. Run your laundry machine and dishwasher once more and flush all toilets again.
This entire process can take quite a long time, sometimes as much as 2 or 3 days, especially with low-production wells where you can’t flush the system as quickly. But once you have completed the flush process, your water should be safe for drinking, bathing, and laundry. If you want to err on the cautious side, purchase a chlorine test kit from a swimming pool shop to directly measure the chlorine level.
Wait a week, and then run another water quality test. Your water should now be bacteria-free. But if the test comes back positive for bacteria, or you start to see signs of water contamination any time within a few months after chlorinating your well, you have a more serious problem that shock chlorination can’t fix. In this case, you need to contact Watson Well and have our professionals service your well.
In less than two months of using water made from Watson’s Ozone Water Treatment System, we are watering our farm with clear pure treated water which actually contains over 300% more dissolved oxygen to all the plants roots. The difference it is made with our crops this year is incredible.
Don Watson and his family have been providing experienced and reliable service to our well-water system since 2011. In those seven years, Watson Well has made a number of timely emergency service calls at any time of day and night, upgraded our water system, and rehabilitated our well.
When our well stopped producing water this summer, I called Watson Well. They used a special pump and opened up the well from 67’ to 132’. While inspecting the well with a video camera, they found that the wells steel casing had deteriorated in a number of places leaving large holes where sand and gravel were continuing to enter the well. They immediately installed a new liner and gravel packed the well. Our well has never produced this much water volume in twenty years of living on this property. We are also noticing a tremendous improvement in the quality of the water.
As Public Works Director for the Bear River Band of the Rohnerville Rancheria, I have contracted with Watson Well on five different projects for the tribe, here in Loleta, CA. Their company has completely replaced both of our main water systems submersible pumps and piping, which was not an easy task, as those wells are very deep. These projects were done very quickly and efficiently, while still maintaining a potable water supply to everyone at all times. They have the tools and equipment to not only handle the small jobs, but large jobs like this also. They have also installed three water softening units for us, as our water is very hard. These are big commercial units and all are working flawlessly. They have also developed a small rural water system for us on a piece of property the tribe recently purchased, to supply water to livestock. All of the work they have done for us is doing what they said it would do, without any problems or issues. Don, his sons, and employees are all very knowledgeable and professional and did our projects at a very reasonable cost. They stand behind their work and are only a phone call away. I would highly recommend Watson Well for any water project, no matter what the size, if you want it done right, on time and on budget, you won’t be disappointed.
It is hard to believe that it has been 9 months since I called you with an “out of water” problem on our property. It is not the call that any one on a well wants to make during a record breaking drought. You were here in a very short time and after taking in all the normal diagnostics you were concerned about us being dry but not convinced it was a true dry well. I think we were very fortunate that you had the ability to put a camera down our well to see what was happening and came up with a plan to rehabilitate our well after you discovered our weep holes for the well were plugged with iron bacteria, calcium and stuff. It gave us hope that we could get this reliable well up and running. You pulled the pump and line and determined that pump was fine. Once that was clear you put in the proper chemicals and literally scrubbed our well pipe of the “stuff” and found that our well was over 200’ deep. Water flowed and once the junk was sucked out of the well bottom and the chemicals neutralized we had 18’ more water which put us at over a 50’ column of water, of course this was fantastic. While here, all new water line and electrical wire was reinstalled and new electronics that were more current and a vast improvement of what we had. Since then the water keeps flowing with generous amounts and quality.
During the past two years, Watson Well has designed, constructed, and maintained a number of different projects at my home. These include new water storage tanks, a water treatment system, new piping from the pump house to the residence along with separate lines and faucets for untreated water; and a complex rain water catchment system including tanks, piping and faucets to different locations, all while providing flexibility directing the water to different areas as needed. Don Watson and his crew worked efficiently and coordinated the different aspects of the jobs in an effective manner. All systems continue to operate as expected without any problems. Don was always extremely helpful and receptive to new ideas which he easily incorporated into the projects.